Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Published (Last):||7 January 2013|
|PDF File Size:||2.59 Mb|
|ePub File Size:||10.61 Mb|
|Price:||Free* [*Free Regsitration Required]|
Starting end on a high inertia, low opposing torque application. This function is only protecting from short-circuits on motor side.
Phases off-balance due to insulation defect on IT rate 1. The starter software version can be seen through a window after additional part disconnection. It’s a community-based project which helps to repair anything.
Version Date of selling V1.
Altistart 46 – Documents and Downloads | Schneider Electric
If the motor runs on RUN order and stops at the 3 stop configurations, without disable, the repair is over. The position of the blue wires is different on an ATS Screws Fan view from above 9 – Disconnect the two power supply wires from the transformer from the fan black wire with white cable end.
Value kept for the altistarh voltage 2 V AC Seco nd ar y: If, for practical reasons, you do not want to disconnect the protection and control circuits, top to bottom terminal resistance can be measured. The quality of the replacement service is based on stocks constituted at Evreux, in the branches and by the official dealers. InF recognition of rating Up to now experience: Connect the cables to the plug-in units according to the following drawing.
Remove the connectors located at the base of the product.
Assembly size 3 Parts list Interconnection drawing Part 4: For wiring J12 and J32 use long cables with connectors so that they can be connected to the plug-in unit furthest to the left of the starter. Check correspondence between motor msnual starter. Over Heat Fault starter thermal protection fault. Thermal state is saved in the eeprom when the network disappears. Possibility of line fuse melting.
Altistart 46 Soft Starters – Documents and Downloads | Schneider Electric
SY3CM Green wire mark 2: LrF Locked rotor Fault Measurement principle: EtF External Fault Measurement principle: Up to now experience: Starter not supplied with current on L1-L2-L3. External fault order Operating state A,tistart to now experience: Minimum resistance has to be 50 kilo-ohms.
Conversion instructions for sizes 4 and 5 Remove the cable from the current transformers by cutting the clamps and unscrewing the connection screws on the transformers.
The second level of telephone assistance is done through the direct line of Global Help Desk: I C 10 1 0 3 6 7 17 18 5-point socket: It requires a fair knowledge of the product and its applications ventilation, pumping, convoying, …. Assembly size 5 Parts list Part 6: To install this software: Avoid the current pulse manuall the engine as well as startup in current control correction of the anomaly concerning a random startup following a series of transient power cutoffs.
If the cables are too short, use the TI ribbon cable which is part of the kit. Observe the orientation of the transformer, placing the cable with connector on the right-hand side when viewing the unit from the front with the transformer fitted on the plate.